0061 RF Occupancy Or Vacancy Sensor Consumer Guide Lutron Electronics
Seek advice from that product’s set up sheet for instructions. Twist and take away mounting bracket to insert battery. Product Description Lutron’s ceiling-mounted Occupancy Sensors are wireless, battery-powered, passive infrared (PIR) units that automatically control lights through RF communication with a dimming or switching gadget. These Sensors detect the heat from folks transferring within an space to determine when the space is occupied. The Sensors then transmit the suitable commands to the associated dimming or switching gadget to turn the lights on or off automatically, offering each comfort and exceptional power financial savings. Sensor doesn't perform satisfactorily from this location, it may be moved to 1.Four Ifanother location by pulling the Sensor straight down and repeating steps 1.3 and 1.4. 1.5 If the Sensor’s performance is satisfactory, it must be completely attached to the ceiling tile, as described in part G. Everlasting Mounting. Momentary Strong Ceiling Mounting Use this process if the Sensor will likely be mounted on a stable, continuous ceiling surface comparable to drywall, plaster, concrete, or wooden. Two 3M™ Command™ adhesive strips are provided for quickly mounting and testing the Sensor on easy, strong ceiling surfaces. These strips are designed for simple, damagefree removing and will not be reusable. These strips shouldn't be used for completely mounting the Sensor (see part G. Everlasting Mounting ). Carefully comply with the elimination instructions beneath to ensure the ceiling shouldn't be broken during removal. Observe: Do not use the adhesive strips on ceiling tiles, as they will doubtless cause injury to the tile upon removing. Easy-to-comply with Directions Set-Up To ensure that the Sensor to function correctly, it should first be arrange with a corresponding dimming or switching device. The process for establishing a Sensor with a Maestro Wireless® (MRF2- only) Dimmer or Electronic Swap is detailed under. P/N 041-172a 2.1 Peel the pink "Command Strips" liner off of one of many adhesive strips and apply the strip to the flat aspect of the mounting bracket as proven in the diagram. Note: Do not cowl the bracket’s screw holes as a result of they will be used to mark screw hole areas on the ceiling. Organising a Sensor with a Maestro Wireless Dimmer or Electronic Switch Dimmer Key Options · Low Upkeep. 10-yr battery life. Convenient low-battery indicator. · A number of Devices. Up to three Sensors can work collectively to control lights for broader coverage in large areas. Every Sensor may be added to up to 10 receiving devices. Sensor Operation Occupancy Version - The Sensor will routinely turn the lights on when the area is occupied and routinely flip the lights off after the area is vacated. The Sensor will robotically turn the lights off after the area is vacated. There's a built-in 15-second vacancy grace period that begins when the lights are routinely turned off, during which the lights will mechanically turn again on in response to movement. This grace period is provided as a security and convenience feature in the event that the lights flip off whereas the room is still occupied, in order that the user does not need to manually turn the lights back on. After 15 seconds, the grace interval expires and the lights should be manually turned on. This Sensor is a part of a system and can't be used to regulate a load with out a suitable dimming or switching device. Discuss with the instruction sheets of the receiving system(s) for set up data. The Sensor may be installed up to 60 ft (18.Three m) away from the associated dimming or switching device(s) if they're in direct line of sight. If there are partitions or other obstacles between the Sensor and receiving machine(s), the Sensor should be positioned within 30 ft (9.1 m). Caution: This product should not be used to manage equipment which could create hazardous situations, comparable to entrapment, if operated accidentally. Sensor in a location where it has a broad view outside the meant space. If that is unavoidable, the lens can be masked to dam the view of undesired areas (refer to part I. Lens Masking). This warranty is in lieu of all different categorical warranties, and the implied guarantee of merchantability is proscribed to at least one year from purchase. This warranty doesn't cowl the cost of set up, removal or reinstallation, or damage ensuing from misuse, abuse, or damage from improper wiring or set up. This warranty doesn't cowl incidental or consequential damages. LUTRON’S Liability ON ANY Declare FOR DAMAGES ARISING OUT OF OR IN CONNECTION WITH THE MANUFACTURE, SALE, Installation, Supply, OR USE OF THE UNIT SHALL By no means EXCEED THE PURCHASE Price OF THE UNIT. This warranty gives you particular legal rights, and chances are you'll have other rights which range from state to state. Some states don't allow the exclusion or limitation of incidental or consequential damages, or limitation on how long an implied warranty could final, so the above limitations might not apply to you. Patents pending. Lutron, Maestro Wireless, and the Sunburst logo are registered trademarks and Radio Powr Savr is a trademark of Lutron Electronics Co., Inc. ANSI is a registered trademark of the American Nationwide Standards Institute. IEC is a trademark of the International Electrotechnical Fee. Made and printed in the U.S.A. 25/09/09 P/N 041-172 Rev. A eight ft (2.Four m) 18 x 18 ft (5.5 x 5.5 m) thirteen ft (4.0 m) 9 ft (2.7 m) 20 x 20 ft (6.1 x 6.1 m) 14.5 ft (4.4 m) 10 ft (3.0 m) 22 x 22 ft (6.7 x 6.7 m) sixteen ft (4.9 m) 12 ft (3.7 m) 26 x 26 ft (7.9 x 7.9 m) 19 ft (5.Eight m) Non permanent Mounting Strategies 1.1 1.2 Insert the ceiling tile mounting wire by way of the 2 smaller holes in the mounting bracket and exchange the mounting bracket. Mount Sensor to a ceiling tile by inserting the wire legs by the tile, ensuring the Sensor is flush to the tile. Notice: Do not twist wire legs collectively. 1.2 After the Sensor has been quickly mounted, go away the Sensor in place on the tile and either take the tile down or remove an adjoining tile to gain entry to the legs of the mounting wire on the back of the tile. Low Activity: This is essentially the most delicate setting and can detect very slight motions. This is the really useful setting, as it'll work nicely for nearly all purposes. It is ideal for spaces the place occupants will usually be seated for long periods of time. Twist the wire legs together tightly so the mounting bracket stays snug in opposition to the tile. This setting is barely less sensitive than the Low Activity setting and can be utilized for areas that experience normal exercise. That is the least sensitive setting and can be used for spaces that can generally solely expertise large motions, resembling foot traffic. The Low Exercise setting is the default and can perform finest for most applications. Not often, if the Sensor is placed close to exterior noise sources equivalent to heating vents, air conditioning vents, or mild bulbs, it could turn the lights on without occupancy or keep the lights on too lengthy after vacancy. If this occurs, altering the sensitivity to Medium Exercise or Excessive Exercise ought to resolve the issue. Replace the tile. Permanent Stable Ceiling Mounting 2.1 2.2 2.3 Advanced Set-Up Operation The advanced set-up is accessed through the use of the buttons on the again of the Sensor. Drill two 3/16 in (4.6 mm) pilot holes for the supplied screw anchors. Press the anchors into the holes and faucet flush with a hammer. To display the current setting, press and launch the specified button. An LED will illuminate briefly, indicating the current setting. Place the flat side of the mounting bracket in opposition to the ceiling and install the two provided screws utilizing a hand screwdriver. To regulate a setting, press and hold the specified button till the LED corresponding to the present setting begins flashing rapidly, indicating the setting can now be adjusted. Every subsequent button press of less than 2 seconds will increment the mode to the next accessible setting. Urgent any of the opposite buttons will don't have any impact. To save the chosen setting, press and hold the button till the LED turns on stable, indicating the saved setting. Through the adjustment process, if there is no activity for 30 seconds, the LEDs will flip off and no settings will be saved. Be aware: Don't over-tighten. 2.Four Attach the Sensor to the mounting bracket by inserting and twisting in a clockwise course till the Sensor locks into place. To remove the bracket from the ceiling, grasp the removing tab on the adhesive strip and pull the tab VERY SLOWLY straight throughout the ceiling, stretching the strip until the bracket releases from the ceiling. Discard the strip. Never pull the strip at an angle, as it might break or injury the ceiling floor. Notice: Do not pull at an angle. Lens Masking (Optionally available) At any time when possible, the Sensor ought to be installed in a location where it can't simply see into areas outside the supposed space, comparable to hallways or adjoining rooms. If this example can't be averted, portions of the lens could also be masked with the offered labels to dam the Sensor’s view of the undesired areas. It's endorsed to remove the Sensor from the mounting bracket before making use of Superior Set-Up (Optionally available) the masking labels. The Sensor options a number of superior set-up modes. For the majority of installations, the default settings will provide the very best efficiency and also you is not going to must make the most of the superior set-up. The Occupancy version of the Sensor has three adjustable superior set-up modes: Timeout, Auto-On, and Sensitivity. The Vacancy-Solely model has only two modes (Auto-On not obtainable). The default settings are listed beneath. The Sensor will be screwed onto the mounting bracket in a number of completely different orientations. Make certain to notice the Sensor’s orientation before taking it down and replace the Sensor in the same orientation to make sure the intended space gets blocked. Outer lens sections correspond to the detection areas furthest away from the Sensor, while internal sections correspond to areas nearer to the Sensor. Watch out when making use of the labels to avoid creating gaps between adjoining masked sections. The Sensor could detect movement by inadvertent gaps. At all times (Occupancy model only) Timeout 30 min 15 min 5 min Auto-On Always Low mild Disable Activity Timeout 30 min 15 min 5 min Advanced Set-Up Modes Auto-On Always Low mild Disable Exercise Activity: Low Activity Lens sections proven in white are masked with labels Timeout The Sensor will turn the lights off if no movement occurs for the duration of the timeout period. There are three out there timeout settings: 5, 15, and half-hour. Lens Mask Lens sections proven in grey have not been masked Auto-On The automatic-on performance of the Sensor could be adjusted to control how the lights respond upon initial occupancy. There are three available settings: Always, Low gentle, and Disable. All the time: The lights will always turn on. Testing Sensor Coverage With the Sensor mounted on the ceiling, press and launch the "Test: Sensor" button on the front of the machine. The lens will glow briefly, indicating the test mode has been entered. Word: There's a heat-up period of roughly forty seconds after the batteries are put in before the test mode may be activated. If the button is pressed during this time, the lens will flash continuously until the warm-up period is complete, after which the check mode will likely be mechanically entered. Affirm the protection space by walking by way of the house and observing the lens. The lens will glow solid each time movement is detected. If the lens remains off throughout movement, the Sensor cannot detect motion at that location. Press and release the "Test: Sensor" button again to exit the check mode. If the button is not pressed, the take a look at mode will robotically outing quarter-hour after being enabled, or 5 minutes after the last detected motion if the room is vacated. If the Sensor has vital bother detecting movement in the course of the check, it needs to be moved to a different location and retested. If the Sensor nonetheless has poor detection from the brand new location, refer to the Troubleshooting part. Temporary Drop Ceiling Mounting Use this procedure if the Sensor will probably be mounted on a ceiling tile. The ceiling tile mounting wire is supplied for each temporary and permanent mounting of the Sensor to drop ceilings composed of a number of tiles. It's designed to allow short-term mounting, testing, and repositioning (if crucial) of the Sensor with out damaging a ceiling tile. Once the Sensor’s closing place has been chosen, the mounting wire can be twisted to lock the Sensor in place completely. If the Sensor protection and wireless communication tests have been successfully accomplished, use the mounting bracket as a template to mark the screw hole locations with a pencil. Observe: Pull very slowly. Max. Room Dimensions Radius of Coverage for Complete Protection at Flooring In case you are uncertain about accurately positioning the Sensor, the next temporary mounting and testing procedures are really useful to confirm correct performance before permanently putting in the Sensor. Sensor’s detection vary is dependent on the ceiling peak, as shown within the desk beneath. Discover: Don't disassemble, crush, puncture, or incinerate the batteries. Don't dispose of batteries in regular family waste. Please recycle, take to a proper battery disposal facility, or contact your native waste disposal provider relating to native restrictions on the disposal or recycling of batteries. O NOT mount the Sensor within 4 ft (1.2 m) of HVAC vents or gentle bulbs put in beneath the ceiling line. Warmer rooms may reduce the Sensor’s capability to detect occupants. Use only high-quality lithium batteries, measurement CR123, 3 V (ANSI-5018LC, IEC-CR17345). Do not use rechargeable batteries. Utilizing improperly rated batteries could damage the Sensor. For questions regarding the set up or operation of this product, name the Lutron Technical Assist Center. Please provide exact mannequin number when calling. U.S.A. and Canada (24 hrs / 7 days) Setting the Occupancy Gentle Degree (occupancy model, dimming devices only) the Sensor to the mounting bracket by inserting and twisting in a clockwise 2.5 Attach direction until the Sensor locks into place. Sensor protection and wireless communication assessments as described in 2.6 Carry out sections E. Testing Sensor Protection and F. Testing Wireless Communication. The Sensor should be put in in a location the place it has a good view of all components of the room. The Sensor requires line of sight to function properly. If you cannot see the Sensor, it cannot see you. The Sensor can not see through glass objects corresponding to patio or shower doorways. The range and efficiency of the RF system is extremely dependent on a variety of advanced elements corresponding to: · Distance between system parts · Geometry of the building construction · Construction of partitions separating system components · Electrical gear located close to system elements Technical Assistance 2.2 Establish a location on the ceiling where the Sensor can have a superb view of the room. 2.Three Remove the black "wall side" liner from the adhesive strip. The Sensor is designed for ceiling use solely. Do not install on ceilings higher than 12 ft (3.7 m) or non-ceiling surfaces. Doing so may considerably inhibit the Sensor’s efficiency. 4. Do not paint Sensor. · · · · The "Lights On" and "Lights Off" buttons ought to now swap the lights in the room on and off, respectively, when pressed. Repeat the above process to set up the Sensor with any extra devices. The Sensor is intended for indoor use only. Function between 32 °F and 104 °F (zero °C and 40 °C). 1.1 several seconds. Sensor that has been set up. After roughly 6 seconds, the lens will flash rapidly several times, indicating the light stage has been saved. All Sensors arrange with the Dimmer will now use the saved occupancy gentle degree. 2. Clear Sensor with a smooth damp cloth solely. Don't use any chemical cleaners. Word: This tools has been tested and located to comply with the limits for a class B digital machine, pursuant to half 15 of the FCC guidelines. These limits are designed to supply reasonable protection towards dangerous interference in a residential installation. This gear generates, makes use of and might radiate radio frequency energy and, if not put in and utilized in accordance with the directions, could cause dangerous interference to radio and tv reception, which can be determined by turning the tools off and on. The user is encouraged to try to correct the interference by one or more of the next measures: Reorient or relocate the receiving antenna. Increase the separation between the tools and receiver. Connect the equipment into an outlet on a circuit completely different from that to which the receiver is linked. Seek the advice of the dealer or an experienced radio/Television technician for help. Warning: Changes or modifications not expressly authorised by Lutron Electronics Co. may void the user’s authority to operate this tools. This gadget complies with Half 15 of the FCC rules. This system should accept any interference obtained, including interference that may cause undesired operation. Swap 2.1 Set the Dimmer to the specified light level for getting into the room. 2.2 Save holding the "Lights On" button on the front of a Note: For either Sensor model, the lights will also be manually turned off at any time through the use of the dimming or switching device instantly. Essential Notes or Add the Sensor to the Dimmer or Switch by pressing and holding the "Lights Off" button on the entrance of the Sensor for roughly 6 seconds until the lens flashes briefly. The lights in the room may even flash three times, indicating the Sensor has been efficiently added. The Dimmer or Change will exit set-up mode robotically. The sensitivity of the Sensor may be adjusted based on the anticipated level of exercise throughout the room. There are three out there activity settings: Low Exercise, Medium Activity, and Excessive Exercise. Everlasting Drop Ceiling Mounting Be aware: Leave the removal tab uncovered previous the sting of the bracket so it may be accessed for removing later. 6 seconds till all LEDs on the device start flashing. Launch the faucet button. Sensor is detecting movement in areas that are not fascinating, similar to hallways or adjoining rooms, consult with part I. Lens Masking. If Sensor detection is passable during this check, perform the wireless communication check as described in section F. Testing Wireless Communication. Testing Wireless Communication This take a look at must be carried out to confirm that the Sensor has been accurately set up with the corresponding dimming or switching device and that there is correct wireless communication from the chosen Sensor location. If the lights within the room aren't on, flip them ON manually at the dimming or switching machine. Press and release the "Lights Off" button on the entrance of the Sensor. The lights ought to flip OFF. Press and launch the "Lights On" button on the entrance of the Sensor. The lights should turn on. If the lights don't respond correctly, refer to the Troubleshooting section. Low mild: The lights will only activate automatically upon entry if there isn't already ample ambient gentle within the room. Hallway falls inside Sensor’s protection area. Disable: This setting converts the Sensor to vacancy mode. The lights will not automatically turn on but will still routinely turn off after vacancy. The lights have to be manually turned on by utilizing the associated dimming or switching machine. Be aware: The 15-second vacancy grace interval is active in this mode. Consult with the Sensor Operation section at the start of this doc for extra particulars. Troubleshooting Symptom Potential Causes Solution Lights don't activate when area is occupied. Sensor is not accurately added to dimming / switching device(s). Sensor’s Auto-On setting is about to "Low light" or "Disable". The lights have been just lately turned off manually and the timeout has not but expired. Sensor does not have full view of room. Sensor is exterior wireless range of dimming/switching gadget. Confer with part B. Set-Up. Check with section H. Advanced Set-Up. Dimming/switching device has been improperly wired. Gentle bulb(s) burned out. Breaker is off or tripped. Sensor’s timeout is simply too short for this utility. Sensor does not have full view of room. Lens mask is improperly utilized. Sensor’s sensitivity is too low. Sensor’s timeout has not yet expired. An external noise supply similar to an HVAC vent is interfering. Check with part A. Pre-Set up. Conduct of lights does not match Sensor settings. Sensor coverage extends beyond room perimeter. The supposed setting was not saved. A number of Sensors are added to a dimming/switching gadget and their settings don't match. Seek advice from part A. Pre-Installation. Seek advice from section C. Sensor Placement or I. Lens Masking. Consult with section H. Superior Set-Up. Refer to part H. Advanced Set-Up. Sensor lens doesn't glow in response to motion during Sensor coverage testing. Sensor can not see movement attributable to obstruction. Room is simply too big or oddly formed. Transfer Sensor to a different location. Discuss with part C. Sensor Placement. Multiple Sensors may be essential for full room coverage. Strive shifting Sensor to a new location or decreasing sensitivity. Discuss with part C. Sensor Placement or H. Superior Set-Up. Lights turn OFF while area is occupied. Lights keep ON after house is vacated. Lens doesn't stop glowing during Sensor protection testing even when there isn't a movement. Lights do not reply accurately during wireless communication testing. Sensor lens flashes and lights do not activate when space is occupied. Battery has been put in incorrectly. An exterior noise source resembling an HVAC vent is interfering. Seek advice from part C. Sensor Placement. Refer to part C. Sensor Placement or F. Testing Wireless Communication. Refer to part H. Advanced Set-Up. Seek advice from section C. Sensor Placement. Confer with section I. Lens Masking. Consult with section H. Superior Set-Up. Check with section H. Advanced Set-Up. Try transferring Sensor to a brand new location or decreasing sensitivity. Confer with part C. Sensor Placement or H. Advanced Set-Up. Sensor will not be accurately added to dimming / switching system. Sensor is outside wireless vary of dimming/switching gadget. Confer with section B. Set-Up. Move Sensor nearer to dimming/switching machine and retry check. Refer to part F. Testing Wireless Communication. Battery has been installed incorrectly. Dimming/switching device has been improperly wired. Light bulb(s) burned out. Breaker is off or tripped. Battery is low. Discuss with part A. Pre-Installation. Take away sensor from check mode. Consult with section E. Testing Sensor Protection.